Although Part P Building regulations require a qualification to undertake extensive electrical work in your own home, minor tasks such as replacing damaged sockets or light switches can be done without having to notify your Local Building Authority Control Department. In this post we'll take you through a few simple steps to replace a plug socket or alternatively change a single one into a double.
Before you start ANY sort of electrical work make sure the power is switched off at the main consumer unit or switch of the relevant circuit breaker and lock it if you can. Then make sure that the circuit is indeed dead using a socket tester. Make sure to also have protective gloves and safety goggles on you at all times.
Also take note that since 2006 the core colours inside electrical cables have changed. In new two-core-and-earth cables, the live/phase core is insulated in a brown sheath as opposed to a red one and the neatural core is now blue rather than black. If you are connecting old and new cables together, take extra care to make sure that the cores are attached by their corresponding colours.
What you will need:
- Socket tester & socket template
- Pipe and cable detector
- Socket faceplate or new double socket
- Wall plugs and screws
- Mounting box
- Green/Yellow pvc sleeving
To change a damaged socket:
Step 1: Confirm you have switched off the main power using your socket tester. Once sure unscrew the socket faceplate and pull it away from the wall. Keep the screws just in case the new ones don't fit.
Step 2: Loosen the terminal screws and release the cable cores. Should the insulation be heat damaged, cut back the cores and strip the ends. If the earth core is bare, cover it with the green/yellow sleeving.
Step 3: Connect the brown (or red) core(s) to the live terminal of the faceplate, the blue (black) ones to the neutral terminal and the earth core to the earth terminal. Tighten the screws fully and fit the new faceplate. When you have turned the power back on, use the socket tester again to check it is wired correctly
To change a single flush socket to a double:
Increasing the number of sockets in a room isn't as difficult as it might sound if you follow these simple steps...
Step 1: Isolate the circuit and then use the socket tester to make sure that it is dead. Unscrew the faceplate and disconnect the cables from the single socket mounting box.
Step 2: Knock out the middle section in the double box and pass the cables through. Mark where the screw holes are on the wall using a pencil, remove the box and drill.
Step 3: Screw the new box in place and connect the cables to the terminals. Fit the new faceplate and then test using the socket tester again once power has been restored.
Hopefully after reading this you'll feel confident enough to do these tasks yourself without having to pay for a professional electrician! However if you're interested in learning more about what electrical tasks you can perform at home with the right training, or alternatively hoping to gain qualifications to become an electrician - look no further than Access Training
's range of bespoke electrical courses
. From Part P
to PAT Testing
and wiring regulations to DIY, we offer something for everyone regardless of age, background or experience.
Contact Access Training on 0800 345 7492 for more information or arrange a visit of our training facilities.